Air Conditioning and Heating Reviews in Litchfield Park, AZ
Alaskan Air Conditioning & Heating prides itself in providing excellent heating and air conditioning services to Litchfield Park AZ residents.
Our reviews from your Litchfield Park AZ neighbors describe the positive impact we’ve had in your community.
for Litchfield Park, AZ
Our Reviews by City
James did a great job
Delores - Litchfield Park, AZ
Milford - Litchfield Park, AZ
William Fiegal did an excellent job. Installation crew had some problems but William came down and fixed things up.
Great Service, Awesome Price
Don - Litchfield Park, AZ
The technician was very informative, understanding and was willing to work with what was best for us in terms of finances and criticality first. Was very kind, and we wish him the greatest of blessings as he blessed us.
Elsie - Litchfield Park, AZ
Great Alaska air service
JAMES - Litchfield Park, AZ
Jason give honest, fair work
Jim - Litchfield Park, AZ
Rheem heatpump maintenance
Diagnostic on carrier split unit.
Could not diagnose unit block of ice on coil
Performed diagnostic on Lennox unit.
Performed diagnostic on unit.
Installing a 5-2-1 compressor saver on a Carrier air conditioner for a first time Alaskan Air Conditioning client
Providing cooling for a first time Alaskan Air Conditioning client and signing an Alaskan Air Conditioning Club Membership
Full inspection on dual rheem split systems for elderly Alaskan club member
Two unit pma. One unit just installed second unit 16 years old had compressor changed roughly 11 years ago. Cleaned outdoor media, very dirty. Made difference with preasures. Still Pressures a little high 50 deg suction and 120 deg high r22 unit ambient 102. Due to age of unit recommend running till it dies then replace or replace before dies out. Do not recommend putting large amount of money into repairs on older r22 unit. Both units running at this time.
One unit post inspection. Tightened Schrader caps and king valves . Unit working great
Unit not cooling
Customer has 2 units in home. East unit is old 3.5 ton gas split system. Gauges are showing bad or clogged txv or orfice. Repair would include removing contaminated refrigerant cleaning or replacing orfice or expansion valve. Cost of repair would roughly be 3k or higher and unit is r22. I do not recommend putting large amount of money into old r22 system. Best option would be to replace unit with higher efficiency unit. Went through pricing and different types of units with customer. He is going to talk with his wife and figure there plan of action. Unit only getting 10 deg split. Once it gets hot unit will not be able to keep up and fail.
Ac tune up on a Lennox split unit
Ac tune up on Rheem split units
Tune-Up Fresh Customer
Ac tune up on a carrier split heat pump
Tune up Bryant ac
Tune up on a carrier furnace
Tune up carrier furnace
Doing a winter tuneup on a Rheem furnace
2 UNIT PMA CHECK, GROUND GAS **MIKE**11/8/2017 11:42:15 AM - SAMANTHA - CUSTOMER RESCHEULED FROM 11/9/17 TO 11/16/1711/14/2017 12:33:07 PM - SAMANTHA - CUSTOMER RESCHEDULED FROM 11/16/17 TO 12/7/17
INSTALLING A HONEYWELL 8000 THERMOSTAT AND DOING AN EVAPORATING COIL CLEAN #CALLALASKAN
Recommending Aeroseal duct seal while doing a fall maintenance tune up for an Alaskan Club Member
Doing a preventative maintenance tune up for a first time customer with a variable speed Trane air conditioner and furnace. Recommending Aeroseal duct seal and a Reme Halo whole home indoor air purification system to optimize efficiency and improve indoor air quality as well as surge protectors to protect the system.
VS MOTOR AND MODULE FAILED AND NEED TO BE REPLACED.