Air Conditioning and Heating Reviews in San Tan Valley, AZ
Alaskan Air Conditioning & Heating provides full service home comfort services, including repair, installation and maintenance, to residents of San Tan Valley, AZ and the surrounding areas.
We’ve been working hard in the San Tan Valley AZ area since 1976. Read our reviews below to find out what your neighbors have recently said about us.
for San Tan Valley, AZ
Our Reviews by City
service contract appointment
ALEX - San Tan Valley, AZ
Very good got to home early after calling did his work and answered any questions
very helpful and informative
GAIL - San Tan Valley, AZ
Earl was willing to go the extra bit to help
TIFFANY - San Tan Valley, AZ
David was kind, explained everything he was going to do and took care of the problem. Great Plumber professional.
ALEX - San Tan Valley, AZ
JEROME - San Tan Valley, AZ
Mike Wilson has awesome customer service quality. He helped find the defaults quick and is very personable. God bless him and your company.
Mario - San Tan Valley, AZ
Friendly service guy
Roger Erlandsen - San Tan Valley, AZ
Called to let me know when he would be here...a real plus for San Tan Valley!
Jason was very helpful and appeared to know what he was talking about
alex - San Tan Valley, AZ
Printed invoice and advertisement somewhat confusing. advertisement indicated 39.95 which included coil cleaning and no trip charge. Invoiced for all three at higher cost??????
Goodman air conditioner summer maintenance Alaskification
Upstairs unit not cooling. Carrier system
York heat pump Alaskification service
Goodman air conditioner Alaskification and recommending Air Scrubber Plus
Tune up on 14 year old system
Tune up on 1 year Lennox split hp
Customer is gathering quotes.
Fresh tuneup on Lennox Heatpump
Replaced contactor on Carrier Alaskan Club Member winter tuneup
Completed a 40 point tune up for an Alaskan customer
Tune up carrier
Performed diagnostic. Put iso pads under compressor and unit. Loosened comp. screws.
Ac tune up on a Goodman split unit
Perform tuneup on trane unit for ACM member. All systems operating within manufacturers specs at this time
2.5 ton split heatpump estimate
System post inspection. Found small amount of oil on condenser pad below king valve. Could not find leak. Cleaned up with soap and water so if new oil comes back we will be able to find were issue is.
AC QUOTE FOR 3.5 TON SPLIT GAS 14 SEER
Doing a preseason maintenance tune up on a York air conditioner for a first time Alaskan Air Conditioning client
AC and heat tuneup on Goodman split unit