Air Conditioning and Heating Reviews in Benson, AZ
Alaskan Air Conditioning & Heating has provided air conditioning and heating services to the residents of Benson, AZ and the surrounding areas since 1976!
Our reviews from your Benson, AZ neighbors tell why we’re the trusted source for heating and air conditioning installation, repair and maintenance.
for Benson, AZ
Our Reviews by City
STAR - Benson, AZ
Very nice, and helpful
WILLIAM - Benson, AZ
Markus, an obviously gifted and knowledgeable rep from Alaskan came out..assessed and clearly explained my needs and options...asking all the right questions without pressure.
Getting ready to perform maintenance on Lennox
Doing a furnace check up
Furnace tune up
Leak search on ac unit
Getting ready to troubleshoot air flow issue on ac system
Diagnostic on air temp ac unit, not cooling
Air conditioning quote
Diagnosing system not cooling
Diagnosing ac system not cooling
Air conditioning quote
Ac tune up
Unit low on charge r22. Customer does not want to pay to recharge. Says Paul was out to do maintenance and unit worked fine before he came out.
Significant other needs to be present for decision. Reschedule for 2 weeks.
FURNACE TYPE-UNIT LOCATION-PMA EXP DATE-PARTS WARR -LABOR WARR -SPECIAL NOTES--DO YOU HAVE A HOME WARRANTY COMPANY--EMAIL ADDRESS-DATE/TIME STAMP--
Found the condensing unit not running... The breaker was tripped, found the CRM grounded out, the contactor is broken and heavily pitted and the disconnect and high voltage wiring is corroded and loose, recommendation is to replace the system due to the age and poor condition it is in to avoid the repair costs and potential costs of future repairs and the system is R22... Split gas coleman trailer style in closet, ground 230v... customer seen alaskan in Costco was interested in those offers and the home depot financing resources were discussed as well... Sending this bid over to sales as a lead so they can more easily finalize financing and best fit for a system, appointment set for Tuesday 10-12a.
Follow up visit from recent PMA visit CFM not operating at the visit... On arrival inspected system and tested in cooling mode for any issues with the system... CFM motor is a variable speed motor which has several safetyâ€™s and communicating parts to it, most likely the ambient thermoster didnâ€™t engage the motor as the temperatures had not reached the point to call for it in the operation at our prior visit, Due to it being 1st call of the morning and mild weather... All testing at this time are good and within range of the manufacturers recommended operating specifications... Service Disconnect was tightened down and secured more properly.